Burden is the load imposed on the secondary of the CT at rated
current and is measured in VA (product of volts and amps). The
accuracy class applies only to loads at rated VA and below, down to
one quarter VA .
The burden on the secondary of a CT includes the effect of pilot
leads, connections etc , as well as the instrument burden
In situations where the meter is remote from the current
transformer, the resistance of the pilot wires may exceed the meter
impedance many times in these cases it is often economical to use 1
amp meters and CTs.
||0.5 - 5VA
||2 - 5VA
||1 - 5VA
||0.2 - 30VA
The diagram below shows the burden imposed on the CT due to a
run of pilot wire. It will be seen that a pilot loop of
2.5mm2 wire, 60 metres long (30 metres distance) has a
load of 12.5 VA on a 5 amp CT but only 0.5VA on a 1 amp CT.
Not sure on how to specify burden we can help, just firstname.lastname@example.org
Other parameters which need to be taken into consideration as part
of the specification: